The Q1 Watermist Suppression System
The Q1 from Q-Fog is a new type of easily installed, enhanced fire protection system developed for existing living environments with a heightened need for fire protection.
E.G. for the elderly, vulnerable, people with dementia or other disabilities in the care sector or in their own home.
The product is specifically designed and fully fire tested to offer a fire protection system that is reliable, simple and cost effective.The basic version of the Q-Fog Q1 shown in the picture offers active fire protection in a room of approx. 25m2.
High pressure water mist technology offers very effective fire suppression while minimising water damage to buildings and belongings.
The Q1 requires no permanent installation allowing for low installation and running costs and minimal maintenance.
Power supply wall socket (230V)
Detection smoke + heat
Active time 15 min
Protected area/volume 25 m2 / 60 m3
Weight (empty) 65 kg
Extinguishing agent 130 litres of water
Installation time app. From 2 to 4 hours
The Q1 can cover extended areas
With the use of additional nozzles we are able to cover mulitple areas or risks.
The unit can be installed within the risk area or in an adjacent room.
Limited for Space?
The Q1 mini is a variant of this without the storage tank, designed to be connected direct onto the incoming domestic water supply.
The Mini comes in two sizes depending on nozzle demand. The standard is 520mm high and the double is 820mm in height. Ideal for concealing in a convenient location.
Examples where the Q1 & Q1 mini
have been used as ‘Engineered design
solutions’ ( EDS ):
• Street Kitchen , kitchens & public areas
• For the protection of lithium batteries
on an electric powered fishing boat
• For the protection of a paper saw at a
paper manufacturing plant
The Q1 unit has been subject to successful full scale fire testing at VTT Technical Research Centre in Finland (2009) and passed its original testing at SINTEF (Now RISE Fire Research Association) Test report #102201.38 of October 3, 2007. The report contains an evaluation of the results reached with Q-Fog AB’s system Q1 in trials performed at SINTEF NBL in October 2005. The tests were performed as a part of the project: “Water mist systems in care homes – A mapping of what effect mobile and easy movable water mist system has on fire safety in care homes”.